How to Use Software WAGO I/O CHECK 3.15 to Test and Configure WAGO I/O System 750
Software WAGO I/O CHECK 3.15 is a Windows application that allows you to operate and display a WAGO I/O System 750's node without connecting to a fieldbus system. You can use this software to read the configuration from the node, display it graphically on the screen, print it with a configuration list as documentation, and specify the process data of the I/O modules. You can also make application-specific settings for some types of interface, Pt100 and thermocouple modules, such as the baud rate or sensor types.
In this article, we will show you how to use Software WAGO I/O CHECK 3.15 to test and configure your WAGO I/O System 750 in a few simple steps.
software wago i o check 3 15
Download Zip: https://www.google.com/url?q=https%3A%2F%2Ftinurll.com%2F2tHabw&sa=D&sntz=1&usg=AOvVaw1aqS5onSW6lYX4diGwYMOt
Step 1: Install Software WAGO I/O CHECK 3.15
You can download Software WAGO I/O CHECK 3.15 from the WAGO website[^1^]. The software is compatible with Windows XP, Vista, 7, 8 and 10. The installation process is straightforward and requires administrator rights. After installation, you will find a shortcut icon on your desktop.
Step 2: Connect Your WAGO I/O System 750 to Your PC
To communicate with your WAGO I/O System 750, you need to connect it to a free serial or USB port of your PC using the communication cable supplied in the set with the system. The communication cable has a USB connector on one end and a SUB-D connector on the other end. The SUB-D connector plugs into the service interface of the coupler or controller of your WAGO I/O System 750.
Step 3: Launch Software WAGO I/O CHECK 3.15
Double-click on the shortcut icon on your desktop to launch Software WAGO I/O CHECK 3.15. The software will automatically detect the connected node and display its configuration on the screen. You can see the node address, firmware version, serial number, hardware version, bus type and module type of each component in your WAGO I/O System 750.
Step 4: Test Your Field Wiring
With Software WAGO I/O CHECK 3.15, you can test your field wiring by displaying and specifying the process data of the I/O modules. You can access this function by clicking on the \"Process Data\" tab at the bottom of the screen. You will see a table with columns for module number, channel number, input/output status, value and unit.
You can toggle the input/output status of each channel by clicking on the corresponding cell in the table. You can also enter a value for each channel by typing in the corresponding cell in the table. The value range depends on the module type and settings. You can check if your sensors and actuators are working properly by observing their reactions to your inputs and outputs.
Step 5: Configure Your Application-Specific Settings
For some types of interface, Pt100 and thermocouple modules, you can configure application-specific settings with Software WAGO I/O CHECK 3.15. You can access this function by clicking on the \"Settings\" tab at the bottom of the screen. You will see a table with columns for module number, parameter name, value and unit.
You can change the value of each parameter by selecting it from a drop-down list or typing it in the corresponding cell in the table. The available parameters depend on the module type and settings. For example, you can change the baud rate, parity, stop bits and data bits for serial interface modules; or change the sensor type, filter time constant and wire break detection for Pt100 and thermocouple modules.
Step 6: Save and Print Your Configuration
After testing and configuring your WAGO I/O System 750 with Software WAGO I/O CHECK 3.15, you can save and print your configuration as documentation. You can access this function by clicking on the \"File\" menu at the top of the screen. You will see options for saving your configuration as a file or printing it as a 0efd9a6b88